|Part #||Model||Dimensions in. (mm)||Weight Capacity UDL (lbs)||Containment Capacity gal. (L)||Weight lbs. (kg)|
|2222||P2 Model||54.5 x 27.3 x 4.3 (1384.3 x 692.2 x 108)||10000 (4535.9)||17.5 (66.2)||56 (25.4)|
|2223||P4 Model||54.5 x 54.5 x 4.3 (1384.3 x 1384.3 x 108)||10000 (4535.9)||35 (132.5)||104 (47.2)|
Frequently Asked Questions
We recommend using a pump (UltraTech part# 2345 can be used) to remove any spilled contents from the sump. (Note: spillage should be pumped into an approved container)
Other than the Spill Deck, you’ll need one Bulkhead Fitting (part# 1073) and one T-Strip (part# 1131) for every 27 1/4” of Spill Deck length that is connected. For example, if you’re connecting a 4-Drum Spill Deck to another 4-Drum Spill Deck you would need two Bulkhead Fittings and two T-Strips. If, on the other hand, you were connecting a 2-Drum Spill Deck on the short end, you would only need one each of the Bulkhead Fitting and T-Strip.
Because of the difference in height, the Spill Deck Plus modules can only be attached to other Spill Deck Plus modules and are not compatible with the standard (5 3/4″ height) Spill Decks.
The Spill Deck that I bought previously does not have any holes to put the Bulkhead Fitting through. Can I drill holes myself?
Yes. All that is required is a 1 9/16” hole saw (1 ½” will also work). On each side of the Ultra-Spill Decks are “dimpled” areas that indicate where holes are to be drilled. Center the hole saw on the area you need to be drilled and carefully cut the hole(s) for your Bulkhead Fittings. File or “flame” any rough or sharp edges prior to connecting.
Sidewall Plugs (part# 2221) can be used if you are no longer connecting a Spill Deck and therefore have a hole that needs to be plugged.
Yes, all grating surfaces on the Spill Decks are slip resistant.
The T-Strips lay across the point where two Spill Decks come together. By “bridging the gap” this piece diverts spills to either of the Decks and keeps any spillage from getting between the units.
One for each 26” of Spill Deck that is being connected.
(Note: The answer to this question is based on one assumption: That the Spill Decks are being used with 55-gallon drums). By themselves, the 2-Drum and 4-Drum Spill Deck Plus units do not meet EPA requirements. They must be connected to another Ultra-Spill Deck to increase the total sump capacity to 55 gallons minimum.
Ultra-Spill Deck Plus Models use a grating that is 52″L x 26″W x 4″H.
Helps Comply with These Rules & Regulations
- EPA Container Storage Regulation 40 CFR 264.175
- Spill Prevention, Control and Countermeasures Rule 40 CFR 12